At American Fire & Security we are continually servicing and maintaining kitchen hood systems and fire doors. One of the most important items for either one of these systems are the fusible links. Per NFPA and the manufacturers standards most fusible link systems must be inspected and maintained every 6 months.
What are Fusible Links?
Fusible links are temperature sensitive fire protection devices designed to be part of a fire protection system. The system is activated when the ambient temperature increases to the point that causes the fusible link to “break-apart”. At the point of breakage, it releases the pre-loaded fire protection device, thus restricting the spread of fire. Fusible links are manufactured under the most rigid quality procedures to assure the highest possible degree of uniformity and “break-away” reliability.
The fusible link is one of the simplest forms of heat detection devices. When links are used in a restaurant system, their purpose is to cause the system to function and extinguish the fire. Fusible links used in this manner are actually releasing devices that are heat actuated. They cause the system to automatically operate at a predetermined “fixed” temperature.
How do they work?
Links are employed to restrain the operation of the system until a fire occurs. Each link is connected by a cable to the restaurant system releasing mechanism. When a high temperature is reached, the two halves of the link separate. When the cable tension is released by the separation of the link, the system operates and wet chemical flows out the discharge nozzles into the fire area.
Why is it important to replace our fusible links?
Fusible Links are one of the most critical components of a kitchen fire suppression system. Many factors can inhibit the fusible link from working properly. NFPA requires the fusible links to be replaced semi-annually, but other factors such as grease build up, could cause the need for them to be replaced sooner.
For more information on Fusible Links or to schedule your next Kitchen Hood System or Fire Door inspection feel free to contact us at (937) 262-7937 or visit our web site!
Functioning Exit Signs and Emergency Lights are vital parts of any building’s safety program. These life-saving pieces of equipment ensure that occupants are able to safely locate points of egress in case of power failure.
Similar to extinguishers, there are fire and life safety codes governing the inspection and maintenance of exit signs and emergency lights.
Many jurisdictions require that emergency lighting systems:
• Are functionally tested monthly for not less than 30 seconds
• Are functionally tested annually for not less than 90 minutes
• Are fully operational for the duration of tests
• Have written records of visual inspections and tests
• Monthly tests and inspections
• Annual tests and inspections
• Written records of inspection
Our technicians are trained to inspect, test, and maintain all of the exit sign and emergency lights in your facility. They can also provide you with the written records you need.
We also carry:
• Replacement Bulbs
• Replacement Batteries
• Other Replacement Parts
• New Exit Signs and Emergency Lights
Ask us for an Exit Sign and Emergency Light Consultation Today!